|Customer :||Brightfams Inc. (Hydronov)|
|Location :||Yardley, PA|
|Product :||Supply Produce to Giant Food Stores|
|Objective :||To provide an engineered chiller/boiler package for a hydroponic temp control
Application with a 40°F – 95°F indoor ambient control range.
Heating Load = 786,234 BTUH
Chilling Load = 60 tons
|Description :||Provided (1) 60 tons refrigerant, (1) 1,000.000 BTUH Boiler and(8) 316 SS grid coil heat exchanger properly sized to exchange (boiler or chiller) 8 ton load per pool pending heating or chilling operational mode.
(3) Pumps properly sized for recirculating chiller & boiler with buffer tanks, properly sized for loading, 115V/60Hz motors.
(1) 300 gallon buffer tank, (1) Air control package preplumbed to include properly sized expansion tanks, Fill-PRV, and air vents.
(10) HEX zone pump packages each pump, check valve and digital temperature controller.
(2) Delta preplumbed equipment skids; (1) preplumbed boiler skid package; (1) preplumbed buffer tank & chiller pump skid. Skids fabrication includes; FRP deck & structural FRP “I” beam, Type “L” copper pipe, BFV and Ball Valves, CPVC SC80 Pipe, Pump Disconnects, and Leak Testing.
|Engineered By :||Rick Murray